1.PCR实验室主体为彩钢板、铝合金型材。房间内部一切阴角、阳角均采取应用铝合金50内圆角铝，易于 处置匆子 侄梦廴尽⒒尽⒉灰浊迳ǖ刃ase。结构坚固，线条简明，美观大方，密封性好。
1. The main parts of the PCR laboratory are coloured steel plate and aluminium alloy profiles. All indoor Yin Angle and Yang Angle are made of aluminium alloy with 50 inner rounded corners, so as to dispose of problems such as easy pollution, dust accumulation and cleaning. Strong structure, concise lines, beautiful and generous, good sealing.
2.准则的三区分隔和气压调理：将PCR过程分红试剂准备、标本制备和PCR扩增检测三个独立的实验区。整个区域有一个整体缓冲走廊。每个独立实验区设置有缓冲区， 再是各区经过气压调理，使整个PCR实验过程中试剂和标本免受气溶胶的污染并降低扩增产物对人员和环境的污染。可翻开缓冲区Ⅰ，缓冲区Ⅱ和 PCR 扩增区的排风扇往外排气，在实验区的外墙上和各扇门上都安装有风量可调的回风口，空气经过回风口向房间内部换气。
2. Standard three-compartment and barometric conditioning: preparation of dividend reagents, preparation of samples and detection of PCR amplification in three independent experimental areas. The whole area has an integral buffer corridor. Each independent experimental area is equipped with a buffer, and each area is regulated by air pressure to protect reagents and samples from aerosol pollution and reduce the pollution of amplified products to people and environment during the whole process of PCR experiment. The exhaust fans of buffer I, buffer II and PCR amplification zone can be opened to exhaust outwards. The air return vents with adjustable air volume are installed on the external walls and doors of the experimental zone, and the air is ventilated indoors through the return vents.
3. Disinfection: Ultraviolet lamps are installed on the top of three experimental zones, three buffer zones and inside the transmission window for disinfection. Mobile ultraviolet lamp is also installed in reagent preparation area and specimen preparation area to stop local disinfection of the experimental table.
4. Mechanical chain stainless steel transmission window: reagents and specimens are transmitted through mechanical chain stainless steel transmission window (electronic chain mode is not recommended) to ensure that reagents and specimens are not contaminated during the transmission process (person shunt).
5. In the air, it is suggested to use PVC coil in the air or in the air of self-leveling plateau, which is of good integrity. Easy to stop cleaning, corrosion resistance. Unqualified can also be used in terrazzo air, or large tiles (at least 800mm * 800mm) joints less than 2 mm.
6. Lighting lamps should be purged to achieve the characteristics of easy cleaning and dust-free. In the process of setting up, we should pay attention to:
Standardized installation process and comprehensive service process.
Installation process strictly designed in accordance with the norms and sciences.
Before installation, it is necessary to confirm the following installation conditions, such as: power supply voltage, position of power supply line, position of telephone network line line, water pressure, minimum installation space, air smoothness, position of ventilation holes, intake pipe and sewer, ideal space size and ventilation port size.
The wonderful content of this article is provided by the knowledge of laboratory decoration. There are many wonderful contents on this website. You can click on more content to enter: . We have a special customer service to answer your questions.