Matters needing attention in installation of high efficiency air supply outlets:
1. Clean the product before installing the high-efficiency air supply outlet, and clean the clean room in an all-round way. If there is dust in the air-conditioning system, it needs to be cleaned and cleaned. It needs to reach the standard of cleaning requirements to clean the interlayer or ceiling interior. After the air-conditioning system is cleaned again, it must run for more than 12 hours continuously. In order to do the cleaning again.
2. The first thing we should know before installation is that the dimension and efficiency requirements of high-efficiency air supply outlet must meet the design requirements of clean room site and customer standards.
3.高效送风口在安装之上，需要现场对送风口的包装进行检查，检查始末包括滤纸、密封胶以及框架，看这些东西有无损坏的环境；边长、对角线和厚度尺寸是否符合吾们的要旨；框架上有无毛刺和锈斑；产品是否有合格证， 技术实现 性能是否符合策划的要旨。
3. Before the installation of the high-efficiency air supply outlet, it is necessary to inspect the packaging of the air supply outlet on the spot, including filter paper, sealant and frame to see if there is any damage to these things; whether the side length, diagonal line and thickness meet our requirements; whether there are burrs and rust spots on the frame; whether the product is qualified, Technology Does the performance meet the design requirements?
4. Safe transportation of high-efficiency air supply outlet should be placed strictly according to the manufacturer's 品牌刺绣. In the process of transportation, it should be handled lightly and avoid violent vibration and collision.
5. Check the leakage of high-efficiency air supply outlet, check and check whether the product is qualified, install according to the size of the resistance of each air supply outlet reasonable allocation, for unidirectional flow air supply outlet, between the same air outlet or the filter on the air supply surface, each rated resistance and the average resistance difference between each set should be less than 5百分比. The cleanliness level should be equal to or higher than that of the 100 level clean room.
7. Clean room needs to install high-efficiency air supply vent flanging and ceiling joints between the implementation of gasket treatment, cracks in the place must be strictly handled. If the high-efficiency air supply outlet damage or coating damage can not be installed again, the air supply outlet and air duct in installation must be strictly connected, the opening end is reinforced with plastic film and tape dense air treatment.
With the summary of the air purification project above, I hope it will be helpful to our customers. If you have any incomprehension or ask for help, please click on our official website: or call for advice. We will try our best to solve it for you.