Modern laboratory is not a laboratory furniture together. It is simply a laboratory, but a system engineering. The overall layout of the experimental space, the experimental area must comply with certain space standards. One or two Do you see that your lab design is standard enough?
1, interior clear height
Routine laboratory and research studio interior height: when the set of air conditioning, not less than 2.70m; set up air conditioning, should not be less than 2.40m. Aisle height should not be lower than 2.20m. Special laboratory interior height shall be determined according to the experimental equipment size, installation and maintenance requirements.
2, the door
A unit composed of 1/2 standard laboratory door width should not be less than 1m, the height of not less than 2.10m. Composed of one or more standard laboratory unit door width should not be less than 1.20m, the height of not less than 2.10m. The special requirements of the room door size shall be determined according to the specific situation. The door fan in the laboratory should have an observation window.
3. The layout of the experimental platform
The common experimental platform is an island or peninsula type central experimental platform, and an experimental platform. It is not suitable to be attached to an experimental platform with a wall outside the window. The island type or the peninsula type central experimental platform should not be arranged in parallel with the outside window. The net distance between the outer wall and the outer wall should not be less than 1.30M when the outer window must be arranged in parallel.
The building of scientific laboratory setting heating and air conditioning should reduce the outer window area on the premise of meeting the requirements of lighting. The outer window of the laboratory setting air conditioning should have good airtight and heat insulation, and the open window fan with no less than the window area of 1/3 should be set.
The standard unit of the conventional laboratory should be determined by the width, layout and spacing of the test rig. The standard unit arranged parallel to the experimental platform should not be less than 6.60m.
If you are interested in our products or have any questions, you can leave a message or contact us directly. We will contact you first time after receiving your information.